The installation of SPDs is often poorly understood. A good SPD, incorrectly installed, can prove of little benefit in real-life surge conditions. The very high rate-of-change of current, typical of a surge transient, will develop significant volt drops on the leads connecting the SPD to the panel or equipment being protected. This can mean higher than desired voltages reaching the equipment during such a surge condition. Prosurge suggests that measures to counteract this effect include locating the SPD so as to keep interconnecting lead lengths as short as possible, twisting these leads together. Using a heavier gauge AWG cable helps to some extent but this is only a second order effect. It is also important to keep protected and unprotected circuits and leads separate to avoid cross coupling of transient energy.